Light up Your World
Question 1: That’s a scary photo of a burnt out electrical fitting. What’s going on?
Answer: Our Sharpe crew was called when a rooftop solar system stopped working. The homeowner noticed a burning smell & a crackling sound coming from the roof.
Q2: What happened next?
A: Our technician used thermal detecting and circuit testing technology to make sure it was safe to work on, and diagnosed that stormwater seeped into the isolator’s casing, shorting out the wiring. This also occurs when hail sets and then melts into the internals. We’ve had similar instances where a shoddy installer left loose wires, which shorted out years later.
Q3: What are some lessons to be learnt from this?
A: Rooftop solar takes the full force of nature but is often neglected because it’s up high and out of sight. All systems should be checked annually by a qualified expert for both safety and performance. Also industry standards have changed in the past few years. For example we replaced that isolating switch with one that met current waterproofing standards. We can supply and install a new quality switch from $330.
Q4: So solar isn’t “set-and-forget”?
A: Certainly not. Yearly inspections often uncover weatherproofing problems like this, storm-damage, inferior-quality panels or even wildlife taking up refuge and chewing wiring. You need your rooftop solar to be harvesting all the energy it can year-round to optimise power bill savings.
Solar Safety Check and Service
Keep your system Solar Safe and at operating at Peak Efficiency with an annual test and service.
Has the wild winter weather taken it’s toll on your Solar System
Maximise your Summer power savings with a comprehensive Solar Power System Test & Panel clean. Let us Inspect, Test & Report on your PV Modules (panels), Railing System, Wiring and Connections, Inverter(s) and Switchboard.